Communication detail settings
Make the settings according to the usage environment.
GOT Net No.
Servo axis switching GD device
5 - 20
5.3 GOT Side Settings
Set the network No. of the GOT.
Set the station No. of the GOT.
Set the GOT port No. for the connection with the Ethernet module.
• For Ethernet(MITSUBISHI ELECTRIC),Gateway
• For Ethernet(FX), Gateway
Set the number of retries to be performed when a communication timeout
When receiving no response after retries, the communication times out.
Specify the time period from the GOT startup until GOT starts the
communication with the PLC CPU.
Set the time period for a communication to time out.
Set the delay time for reducing the load of the network/destination PLC.
Set the servo axis switching GD device head No.
For details, refer to the following POINT.
(3) Indirect specification of the servo axis No.
To connect the GOT with the Ethernet module (Q Series) in the one-on-one relationship using a cross cable, set [Timeout Time] to
6sec. or longer.
Each of [GOT Station] set in the communication detail setting and [Station] set in the Ethernet setting must be set to different
5.3.4 Ethernet setting
The range is 1 to 64 when [Driver] is set to [Ethernet(FX), Gateway].
When connecting to the QCPU, LCPU, do not set  for the port No. Otherwise, monitoring becomes unavailable.
1 to 239
1 to 120
1024 to 5010,
5014 to 65534
(Except for 5011 to 5013 and 49153 to
0 to 5times
3 to 255sec
1 to 90sec
0 to 10000
<For GT27, GT25, GT23>
0 to 65520
<For GT21, GS>
0 to 2032