19.5 Setting of Energy Measuring Unit/
Electric Multi-measuring Instrument
For details of the energy measuring unit/electronic
multi-measuring instrument, refer to the following
Energy measuring unit/Electronic multi-
measuring instrument User's Manual
Energy measuring unit
Electric multi-measuring instrument
19.5.1 Connecting to an energy
Make the communication settings with the front
operation switch on the energy measuring unit/
electronic multi-measuring instrument.
9600bps, 19200bps, 38400bps
1 to 247
Indicates only the transmission speeds that can be set on
the GOT side.
Adjust the settings with GOT settings.
19 - 10
19. ENERGY MEASURING UNIT/ELECTRIC MULTI-MEASURING INSTRUMENT CONNECTION
19.5 Setting of Energy Measuring Unit/Electric Multi-measuring Instrument
19.5.2 Station number setting
In the MODBUS network, a maximum of 31 energy
measuring units/electronic multi-measuring instruments
can be connected to 1 GOT.
Assign a non-overlapped station number ranging from 1 to
247 arbitrarily to each energy measuring unit/electronic
In the system configuration, the energy measuring unit/
electric multi-measuring instrument with the station number
set with the host address must be included. The station
number can be set without regard to the cable connection
order. There is no problem even if station numbers are not
Examples of station number setting