(b) Network Configuration Settings
Reserved/Error Invalid Station
Be sure to set it to perform the cyclic transmission.
(1) When changing the unit parameter
After writing unit parameters to the PLC CPU, turn
the PLC CPU OFF then back ON again, or reset
the PLC CPU.
(2) GOT station type
Set the GOT as an intelligent device station.
12 - 12
12. CC-Link IE FIELD NETWORK CONNECTION
12.4 PLC Side Setting
: As necessary
: Not necessary
(c) Routing setting
Up to 238 [Target Station Network No.]s can be set.
However, the same target station network number
cannot be set twice or more (multiple times).
Therefore, the one that can access to other station
from the request source host GOT is 238 kinds of
[Target Station Network No.]s.
Target Station Network No.
Relay Station Network No.
Relay Station No.
Routing parameter setting of request source
Routing parameter setting is also necessary for the
request source GOT.
For the setting, refer to the following.
11.3.3 Routing parameter setting
1 to 239
1 to 239
1 to 120