Specify the number for [Network No.] and [Station
No.] same as the number assigned to the Ethernet
Specify the IP address for [IP Address] same as the
IP address assigned to the built-in Ethernet port
QCPU or Ethernet module.
The screen returns to the [Connection Channel
Setup]. Click [Connection Test] to check if GX Works3
has been connected to the RCPU.
(b) When connecting to FX5U/FX5UC
[Specify Connection Destination] in
The [Specify Connection Destination 1] is displayed.
Set the [Specify Connection Destination 1]:
PC side I/F
PLC side I/F
Other Station Setting
: Serial USB
: No Specification
Double-click [Serial USB] of the PC side I/F to display
[PC side I/F Serial Setting].
Check-mark either of the following in [PC side I/F
When connecting the GOT and PC with serial
Mark the [RS-232C] checkbox.
When connecting the GOT and PC with USB
Double-click [GOT] of the PLC side I/F to display
[PLC side I/F Detailed Setting of GOT].
On the [PLC side I/F Detailed Setting of GOT], mark
the [via GOT (Ethernet) transparent mode] checkbox
and click [Setting...].
23. FA TRANSPARENT FUNCTION
23.6 Personal Computer Side Setting
23 - 49