Specify the number for [Network No.] and [Station
No.] same as the number assigned to the Ethernet
Specify the IP address for [IP Address] same as the
IP address assigned to the built-in Ethernet port
QCPU or Ethernet module.
Successfully connected with the R12CCPU-V
The screen returns to the [Connection Channel
Setup]. Click [Connection Test] to check if GX Works3
has been connected to the R12CCPU-V.
23.6.3 Accessing the PLC by the GX
Developer, PX Developer, GX
The setting method for the FA transparent function of GX
Developer is used as an example.
GX Configurator is an add-on software of GX Developer.
(Except for GX Configurator-QP)
Connecting the GOT and PLC in bus
connection or direct CPU connection
(when connecting to QCPU (Q mode))
[Transfer Setup] in GX Developer.
The [Transfer Setup] is displayed.
Set the [Transfer Setup]:
PC side I/F
: Serial USB (COM)
PLC side I/F
: PLC module
: No specification
Double-click [Serial] of the PC side I/F to display [PC
side I/F Serial setting].
Check-mark either of the following in [PC side I/F
When connecting the GOT and PC with serial
When connecting the GOT to PC via modem
Mark the [RS-232C] checkbox.
When connecting the GOT and PC with USB
Mark the [USB] checkbox.
23. FA TRANSPARENT FUNCTION
23.6 Personal Computer Side Setting
23 - 53