■2. OMRON Digital temperature controller
Set this item when change the transmission speed used for
communication with the connected equipment.
Set this item when change the data length used for communication
with the connected equipment.
Specify the stop bit length for communications.
Specify whether or not to perform a parity check, and how it is
performed during communication.
Set the number of retries to be performed when a communication
Set the time period for a communication to time out.
Specify the host address (station No. of the GOT to which the
temperature controller is connected) in the connected network.
Set this item to adjust the transmission timing of the communication
request from the GOT.
Select the communication format.
format 1: only continuous access
format 2: continuous and random access
(1) Delay Time
When connecting to the temperature controller E5ZN, set the delay time to 5ms or more.
(2) Format setting
Make sure to select format 1 when connecting with previous models (manufactured in
December 2007 or before) of the THERMAC NEO series (E5AN, E5CN, E5EN, E5GN).
For the continuous access and random access of the temperature controller, refer to the
User's Manual of the OMRON temperature controller
(3) Communication interface setting by the Utility
The communication interface setting can be changed on the Utility's [Communication
Settings] after writing [Communication Settings] of project data.
For details on the Utility, refer to the following manual.
GOT2000 Series User's Manual (Utility)
(4) Precedence in communication settings
When settings are made by GT Designer3 or the Utility, the latest setting is effective.
5.4 GOT Side Settings
9600bps, 19200bps, 38400bps,
0 to 5times
1 to 30sec
0 to 99
0 to 300 (ms)
5 - 25