c) REMOTE DEVICES: DEVICE ID FOR RECEIVING GSSE MESSAGES
Remote devices are available for setting purposes. A receiving relay must be programmed to capture messages from only
those originating remote devices of interest. This setting is used to select specific remote devices by entering (bottom row)
the exact identification (ID) assigned to those devices.
, restart the unit when you change this setting to ensure that the Online or Offline status displays
REMOTE DEVICE 1 ID
REMOTE DEVICE 1 ETYPE APPID
sages. This setting identifies the Ethernet application identification in the GOOSE message. It should match the corre-
sponding settings on the sending device.
REMOTE DEVICE 1 DATASET
DNA and UserSt bit pairs), or one of the configurable datasets.
Note that the dataset for the received data items must be made up of existing items in an existing logical node. For this rea-
son, logical node GGIO3 is instantiated to hold the incoming data items. GGIO3 is not necessary to make use of the
received data. The remote input data item mapping takes care of the mapping of the inputs to remote input FlexLogic™
operands. However, GGIO3 data can be read by IEC 61850 clients.
REMOTE INPUT 1
Remote Inputs that create FlexLogic™ operands at the receiving relay are extracted from GSSE/GOOSE messages origi-
nating in remote devices. Each remote input can be selected from a list consisting of: DNA-1 through DNA-32, UserSt-1
through UserSt-32, and Dataset Item 1 through Dataset Item 32. The function of DNA inputs is defined in the IEC 61850
specification and is presented in the IEC 61850 DNA Assignments table in the Remote outputs section. The function of
UserSt inputs is defined by the user selection of the FlexLogic™ operand whose state is represented in the GSSE/GOOSE
message. A user must program a DNA point from the appropriate FlexLogic™ operand.
Remote input 1 must be programmed to replicate the logic state of a specific signal from a specific remote device for local
use. This programming is performed via the three settings shown above.
setting allows the user to assign descriptive text to the remote input. The
REMOTE INPUT 1 ID
selects the remote device which originates the required signal, as previously assigned to the remote device via the setting
(see the Remote devices section). The
REMOTE DEVICE (16) ID
GSSE/GOOSE message required.
Remote Device 1
ETYPE APPID: 0
setting is only used with GOOSE messages; they are not applicable to GSSE mes-
setting provides for the choice of the L60 fixed (DNA/UserSt) dataset (that is, containing
REMOTE INPUT 1(32)
L60 Line Phase Comparison System
REMOTE DEVICE 1(16)
Range: up to 20 alphanumeric characters
Range: 0 to 16383 in steps of 1
Range: Fixed, GOOSE 1 through GOOSE 16
Range: up to 12 alphanumeric characters
Range: Remote Device 1 to Remote device 16
Range: None, DNA-1 to DNA-32, UserSt-1 to UserSt-32,
Config Item 1 to Config Item 32
Range: On, Off, Latest/On, Latest/Off
Range: Disabled, Enabled
setting selects the specific bits of the
REMOTE IN 1 ITEM
5.7.6 REMOTE INPUTS
REMOTE IN 1 DEVICE