4.2 EXTENDED ENERVISTA UR SETUP FEATURES
Once the template has been applied, users will only be able to view and edit the FlexLogic™ entries not locked by the tem-
plate. The effect of applying the template to the FlexLogic™ entries in the above procedure is shown below.
Typical FlexLogic™ entries without template applied.
Figure 4–8: LOCKING FLEXLOGIC ENTRIES THROUGH SETTING TEMPLATES
The FlexLogic™ entries are also shown as locked in the graphical view (as shown below) and on the front panel display.
b) LOCKING FLEXLOGIC™ EQUATIONS TO A SERIAL NUMBER
A settings file and associated FlexLogic™ equations can also be locked to a specific UR serial number. Once the desired
FlexLogic™ entries in a settings file have been secured, use the following procedure to lock the settings file to a specific
Select the settings file in the offline window.
Right-click on the file and select the Edit Settings File Properties item.
Figure 4–9: SECURED FLEXLOGIC™ IN GRAPHICAL VIEW
L60 Line Phase Comparison System
locked with template via
Template Mode > View In Template Mode
4 HUMAN INTERFACES