4.1 ENERVISTA UR SETUP SOFTWARE INTERFACE
RS485 COM2 Baud Rate
RS485 COM2 Parity
COM2 Minimum Response Time
RRTD Slave Address
RRTD Baud Rate
IP Subnet Mask
Gateway IP Address
Ethernet Sub Module Serial Number
Network Address NSAP
IEC61850 Config GOOSE ConfRev
When a settings file is loaded to a L60 that is in-service, the following sequence occurs:
The L60 takes itself out of service.
The L60 issues a
The L60 closes the critical fail contact.
c) CREATING AND EDITING FLEXLOGIC™
You can create or edit a FlexLogic™ equation in order to customize the relay. You can subsequently view the automatically
generated logic diagram.
d) VIEWING ACTUAL VALUES
You can view real-time relay data such as input/output status and measured parameters.
e) VIEWING TRIGGERED EVENTS
While the interface is in either on-line or off-line mode, you can view and analyze data generated by triggered specified
parameters, via one of the following
The event recorder captures contextual data associated with the last 1024 events, listed in chronological order from
most recent to oldest.
The oscillography waveform traces and digital states are used to provide a visual display of power system and relay
operation data captured during specific triggered events.
f) FILE SUPPORT
Execution: Any EnerVista UR Setup file which is double clicked or opened will launch the application, or provide focus
to the already opened application. If the file was a settings file (has a URS extension) which had been removed from
the Settings List tree menu, it will be added back to the Settings List tree menu.
Drag and Drop: The Site List and Settings List control bar windows are each mutually a drag source and a drop target
for device-order-code-compatible files or individual menu items. Also, the Settings List control bar window and any
Windows Explorer directory folder are each mutually a file drag source and drop target.
New files which are dropped into the Settings List window are added to the tree which is automatically sorted alphabet-
ically with respect to settings file names. Files or individual menu items which are dropped in the selected device menu
in the Site List window will automatically be sent to the on-line communicating device.
g) FIRMWARE UPGRADES
The firmware of a L60 device can be upgraded, locally or remotely, via the EnerVista UR Setup software. The correspond-
ing instructions are provided by the EnerVista UR Setup Help file under the topic "Upgrading Firmware".
major self-test error.
UNIT NOT PROGRAMMED
L60 Line Phase Comparison System
4 HUMAN INTERFACES