# GE L60 Instruction Manual Page 208

Line phase comparison system, ur series.

5.3 SYSTEM SETUP
b) VOLTAGE BANKS

PATH: SETTINGS
SYSTEM SETUP
 VOLTAGE BANK F5
One bank of phase/auxiliary VTs can be set, where voltage banks are denoted in the following format (X represents the
module slot position letter):
Xa, where X = {F} and a = {5}.
See the Introduction to AC sources section at the beginning of this chapter for additional details.
With VTs installed, the relay can perform voltage measurements as well as power calculations. Enter the
5
made to the system as "Wye" or "Delta". An open-delta source VT connection would be entered as "Delta".
NECTION
The nominal
PHASE VT F5 SECONDARY
voltage is applied to the VT primary.
NOTE
For example, on a system with a 13.8 kV nominal primary voltage and with a 14400:120 volt VT in a delta connec-
tion, the secondary voltage would be 115; that is, (13800 / 14400) × 120. For a wye connection, the voltage value
entered must be the phase to neutral voltage which would be 115 /
On a 14.4 kV system with a delta connection and a VT primary to secondary turns ratio of 14400:120, the voltage
value entered would be 120; that is, 14400 / 120.
5-70

AC INPUTS
PHASE VT F5
CONNECTION: Wye
PHASE VT F5
MESSAGE
SECONDARY: 66.4 V
PHASE VT F5
MESSAGE
RATIO: 1.00 :1
AUXILIARY VT F5
MESSAGE
CONNECTION: Vag
AUXILIARY VT F5
MESSAGE
SECONDARY: 66.4 V
AUXILIARY VT F5
MESSAGE
RATIO: 1.00 :1
voltage setting is the voltage across the relay input terminals when nominal
L60 Line Phase Comparison System
VOLTAGE BANK F5
Range: Wye, Delta
Range: 25.0 to 240.0 V in steps of 0.1
Range: 1.00 to 24000.00 in steps of 0.01
Range: Vn, Vag, Vbg, Vcg, Vab, Vbc, Vca
Range: 25.0 to 240.0 V in steps of 0.1
Range: 1.00 to 24000.00 in steps of 0.01
3
= 66.4.
5 SETTINGS
PHASE VT F5 CON-
GE Multilin  