Ethernet communication (FR-F800-E)
Information about the inverter can be monitored by setting the special monitor selection No. of the
instruction code and monitor code using the remote registers, RWw0 and RWw4 to 7.
● For the monitor code (RWw0), select the first monitor description (RWr0) from the lower 8 bits and
the second monitor description (RWr1) from the upper 8 bits.
When output current is selected for the first monitor (RWr0) and running speed is selected for the
second monitor (RWr1), the monitor code (RWw0) is H0602.
● When Pr. 544 = "12, 14, or 18", descriptions of monitor codes 3 (RWw4) to 6 (RWw7) can be selected.
Tab. 5-349: Codes for selecting monitor items
The monitor codes from H01 and up and their contents are the same as those of the RS-485 com-
munication dedicated monitor.
For the details of the monitor code and monitor description, refer to page 5-198.
When the remote registers RWw0 and RWw4 to 7 are used for monitoring, H00 (output frequency),
H01 (output frequency), and H05 (set frequency) always indicate the frequency regardless of the
settings of Pr. 37, and Pr. 144.
5 - 624
description (first 8 bits)
First, third to sixth monitor
description (last 8 bits)
No monitoring (monitor
value is 0)
0.01 A/0.1 A