The housing base is designed for snap-
mounting on DIN rails, type EN50022-35 x
7.5 (can be released with a screwdriver).
8 / 16
The room controllers can be mounted in any orientation, and fixed as follows:
There are two drill holes for screw-mounting (see "Dimensions"
for drilling template). The housing base is fitted with raised
Screws: Max. diameter 3.5 mm, min. length 38 mm
Tightening torque for fixing screws max. 1.5 Nm
When mounting note the following:
The controller should not be freely accessible after mounting. It must be
mounted in a cabinet or behind a cover that can only be opened / removed with
a key or a tool.
Ensure adequate air circulation to dissipate
heat generated during operation.
Easy access is required for service personnel
Local installation regulations must be observed.
Mounting instructions and a drilling template are printed on the controller
The RXB24.1 room controller is commissioned with either the ETS3 Professional or
the Synco ACS tool
via the RS232-KNX / EIB interface, or
via the USB-KNX / EIB interface (OCI700),
or with the HandyTool" via PPS2
The definitive application and the controller's location are handwritten in the
labeling fields "Appl." and "Loc" in the commissioning stage.
A special test mode (ETS3 Professional and HandyTool) is available for operation
of the outputs and interrogation of the inputs.
RXB24.1 – Room controller
02 Apr 2010