4.1 ENERVISTA 650 SETUP SOFTWARE INTERFACE 4 HUMAN INTERFACES. SETTINGS & ACTUAL VALUES
To start communicating with the relay go to ‚"Communication>Computer>Computer settings" section in the main
EnerVista 650 Setup menu.
Safety instructions must be followed before connecting the computer to the relay. Safety instructions are detailed in section
1.1.3. Connect the relay ground terminal and the communicating computer to a good grounding. Otherwise, communication
may not be viable, or even, in worst cases, the relay and/or the computer could result damaged by overvoltages.
For on-line working, previously ensure that all relay communication parameters, such as baudrate, slave ModBus address,
etc., match the computer settings.
The ‚"Communication > computer" screen is divided in several subsections:
Computer settings: Main communication parameters for serial communication and control type selection.
ModBus/TCP Setup (if ModBus /TCP is selected as control type): Communication parameters for ModBus TCP
Communication control: Device communication status (communicating or not communicating).
Communication optimization: allows optimizing the communication time outs and failure establishing.
Figure 4–2: COMMUNICATION PARAMETERS MENU
F650 Digital Bay Controller
4.1.4 COMMUNICATION MENU