GE Oil & Gas Masoneilan * SVI * II AP Advanced Performance Digital Positioner Bench Quick Start (Rev C) Instruction Manual GE Data Classification: Public...
PROBLEMS ARISE WHICH ARE NOT COVERED SUFFICIENTLY FOR THE CUSTOMER/OPERATOR'S PURPOSES THE MATTER SHOULD BE REFERRED TO GE. THE RIGHTS, OBLIGATIONS AND LIABILITIES OF GE AND THE CUSTOMER/OPERATOR ARE STRICTLY LIMITED TO THOSE EXPRESSLY PROVIDED IN THE CONTRACT RELATING TO THE SUPPLY OF THE EQUIPMENT.
Autotune on a bench. Additionally, this document also provides guidance on when to run signatures and produce associated reports. This procedure uses GE’s ValVue* 3 software (ver. 3.20 or later) and the SVI II AP DTM (ver. 2.10.1 or later).
Loop Calibrator (with wall power supply and loop test lead wires) and either a USB connector or a serial port connector for your laptop. The setup shown in Figure 1 is a GE product and can be purchased at: https://www.gemeasurement.com/test-calibration/calibrators/ups-iii-loop-calibrator-ma-v ®...
Fax: 88+91-11-5-1659635 Fax: 88+65-6861-7172 Fax: 88+1-281-671-1735 Jacksonville, Florida Phone: +1- 844-VALVE-GE www.geoilandgas.com/valves *Denotes a registered trademark of the General Electric Company. Other company names and product names used in this document are the registered trademarks or trademarks of their respective owners.