Mounting and assembling a station
5.1 Mounting and assembling a station
22 | 118
Before mounting and installation, check all the fire detection installation
components visually for damage caused by improper transport.
Figure 3: Unpacking and checking
Components with clear signs of damage must not be used in the station or
operated as fire detection installation components.
National and local standards and requirements must be observed when
assembling the station and its components.
The following mounting instructions refer to the specifications of the EN 54
standard and the manufacturer's recommendations.
The site chosen to assemble the station and associated components must
match the planning documents for the fire detection installation.