Figure 27: Wiring example of C-NET detector devices on stub
(1) If shielded connection cables are used, the cable shielding must be connected
on one side.
* The number of connectable C-NET devices and the max. line length depend on
the device connection factor. The maximum number of 126 C-NET devices per
loop and the max. length of line of 3300 m may be reduced significantly depending
on the type and volume of line devices. (Calculation must be performed using
'Quantity Tool' software).
C-NET detector line
65 | 118