Module Parameter Setting of the Master Station
The following parameters are required to use the safety remote I/O module. The parameters are automatically set when a
safety remote I/O module is added in the "Network Configuration Settings". Change the start number and end number of the
RX/RY Setting or RWw/RWr Setting as necessary.
• When using the safety remote I/O module, always enable "Station-based Block Data Assurance" of the
master station. When it is disabled, correct operation of the safety remote I/O module cannot be
guaranteed. For the station-based block data assurance, refer to the following.
MELSEC iQ-R CC-Link IE Field Network User's Manual (Application)
MELSEC iQ-R Simple Motion Module User's Manual (Network)
• Do not set the module parameters using the CCPASET instruction in the master station. Correct operation
of the safety remote I/O module cannot be guaranteed because the module operates with the Station-based
Block Data Assurance disabled when the CCPASET instruction is executed.
• Even though the number of points in the RX/RY Setting or RWw/RWr Setting and that in a safety remote I/O
module differ, an error does not occur on the module. For example, when the number of points in the RX/RY
Setting is set to 16 in a configuration with a safety remote I/O module, only the first 16 points are refreshed.
8 PARAMETER SETTINGS
8.1 Module Parameter Setting of the Master Station
Set the station number of the safety remote I/O module.
Set "Remote Device Station".