When installing the safety remote I/O module, provide a clearance between the module and the sides of neighboring
structures or parts to ensure good ventilation, avoid interference, and avoid stress on waterproof connectors.
To insert or remove a communication connector, provide a clearance sufficient to use a screwdriver.
When using a right-angle, waterproof connector or a Y branch connector, provide a clearance to avoid stress on cables.
(1) 0mm or longer
(2) 50mm or longer
The safety remote I/O module can be installed in six directions.
Fix the module with screws.
6 INSTALLATION AND WIRING
6.2 Installation Environment and Installation Position