4.4.1 Field Setting from Remote Control
Individual function of indoor unit can be changed from the remote control. At the time of
installation or after service inspection / repair, make the local setting in accordance with the
Wrong setting may cause malfunction.
(When optional accessory is mounted on the indoor unit, setting for the indoor unit may be
required to change. Refer to information in the option handbook.)
188.8.131.52 Wired Remote Control <BRC1C61, 62>
1. When in the normal mode, press the "
2. Select the desired MODE NO. with the "
3. During group control, when setting by each indoor unit (mode No. 20, 22 and 23 have been
4. Push the "
5. Push the "
6. Push the "
7. Push the "
If during group setting and the time to clean air filter is set to FILTER CONTAMINATION,
HEAVY, SET MODE NO. to "10" FIRST CODE NO. to "0", and SECOND CODE NO. to "02".
FIELD SET MODE is entered.
selected), push the "
operation is unnecessary when setting by group.)
" upper button (4) and select FIRST CODE NO.
" lower button (5) and select the SECOND CODE NO.
" button (6) once and the present settings are SET.
" button (7) to return to the NORMAL MODE.
" button for a minimum of four seconds, and the
" button (2).
" button (3) and select the INDOOR UNIT NO to be set. (This