(2) After piping work is finished, check drainage flows smoothly.
WHEN ELECTRIC WIRING WORK IS FINISHED
! Check drainage flow during COOL running, explained under "TEST OPERATION".
WHEN ELECTRIC WIRING WORK IS NOT FINISHED
! Remove the electric parts box lid, connect a power supply and remote control to the
! Next, press the inspection / test operation button "
! Be careful when doing so because the fan is turning at the same time.
! Attach the electric parts box lid as before.
Open the water inlet lid, add approximately 2.5 liter of water gradually and check drainage
(Refer to the "HOW TO CONNECT WIRINGS")
Be sure attach the electric parts box lid before turning on the power.
engage the test operation mode. Press the operation mode selector button "
selecting FAN OPERATION "
fan and drain pump will start up. Check that the water has drained from the unit. Press "
to go back to the first mode.
Drain piping connections
Do not connect the drain piping directly to sewage pipes that smell of ammonia. The
ammonia in the sewage might enter the indoor unit through the drain pipes and corrode the
Keep in mind that it will become the cause of getting drain pipe blocked if water collects on
Water inlet lid
phase power supply
" on the remote control. The unit will
". Then, press the ON / OFF button "
". The indoor unit