22.214.171.124 Centralized Control Group No. Setting
In order to conduct the central remote control using the central remote control and the unified
ON/OFF controller, Group No. settings should be made by group using the operating remote
Make Group No. settings for central remote control using the operating remote control.
1. While in normal mode, press and hold the "
2. Select the MODE No. "00" with the "
3. Use the "
4. Press "
5. Press "
! For infrared remote control, see the following.
! For setting group No. of HRV and wiring adapter for other air conditioners, etc., refer to the
Enter the group No. and installation place of the indoor unit into the attached installation table.
Be sure to keep the installation table with the operation manual for maintenance.
more to set the system to "Field Setting Mode".
" button to select the group No. for each group.
(Group numbers increase in the order of 1-00, 1-01, ... 1-15, 2-00, ... 4-15.)
" to set the selected group No.
" to return to the NORMAL MODE.
instruction manual attached.
"switch for a period of four seconds or