Master Module Operation Mode Setting
Set the number of transmission points of the master module.
● Making switch settings in Page 54, Section 7.1.2 enables the number of transmission points to be changed and allows
the transmission cycle time to be shorten in comparison with that of the default setting. ( Page 29, Section 3.2.3 (1))
● The switch settings made become effective when the CPU module is reset or the power is turned off then on again after
writing to the CPU module is finished.
Master module addition
Add the model name of the master module to be used on the project.
(1) Addition method
Open the "New Module" window to add.
Project window [Intelligent Function Module] Right click [New Module]
Set the "AnyWireASLINK Interface Module".
Set the module name to be connected.
Mounted Slot No.
Set the slot No. where the target module is mounted.
The start I/O number (hexadecimal) of the target module
Specify start XY address
corresponding to "Mounted Slot No." has been set. A different address
can be also set.
Set a title.
CHAPTER 7 VARIOUS SETTINGS