Automatic address detection execution timing
The following is automatic address detection execution timing.
Turn on Automatic address detection
the SET switch.
Automatic address detection flag
No ID setting or ID in use detected
Parameter access completion flag
Parameter access error
After turning on Automatic address detection command (Yn1), check that Automatic address detection flag (X(n+1)4) is
turned on or check the SET LED status. Then, turn off Automatic address detection command (Yn1) with a program.
There is no status flag that indicates whether modules with no ID setting or the same IDs are being detected. The
execution duration is approximately 0.5 seconds after the SET LED turns off.
or press and hold
Automatic address detection
Batch read executed
A parameter access
error has occurred.