To ensure more stable transmission quality, connect a terminating unit to the end of a transmission cable (DP, DN).
Terminating unit connection
Connect at least one terminating unit for one AnyWireASLINK line. Connect it at the farthest end from the master module.
Branch of transmission cables (DP, DN)
Connect one terminating unit at the end of a branch line that exceeds 40m.
The total length of the transmission distance for the AnyWireASLINK system can be calculated from A + B.
Note that the total length should not exceed the maximum transmission distance set for the system to branch lines.
The end of a line
at the end
Terminating unit The end of a line
Branch line: 40m or longer