Link/ Active (
Hardware Configuration of EPM
Refer to the common
Hardware Configuration of IO
Refer to the I/O module type section.
ATTENTION: If Secure Communication is enabled in the system, the relative
information of the new CPM should be updated in the IPsec configuration of the
PC installed the ControlEdge Builder and IPsec should be configured and
enabled on the new CPM. For more information, see "Chapter 9 " in the
ControlEdge PLC and ControlEdge RTU Network and Security Planning Guide.
Replacing a non-redundant or unsynchronized
Before replacing a non-redundant or unsynchronized primary PLC-
ATTENTION: This procedure can only be performed while off-
We recommend that you proceed with extreme caution
whenever replacing any component in a control system. Be
sure the system is offline or in a safe operating mode.
Component replacements may also require downloading
appropriate configuration data to the replaced component
through ControlEdge Builder.
Wear an ESD wrist strap and observe static precautions.
It is recommended to upload and SAVE a copy of the
configuration, or ensure that a previously saved copy of the
On for connection; Off for no
connection; and blinking for activity