Network Configuration Setting
Set the parameters of the I/O module with the network parameters written to the CPU module of the master station. When
using I/O modules, for the communication cycle interval setting in "Basic Period Setting" of "Communication Period Setting" in
"Basic Settings" for the network parameters, set as follows.
Communication cycle interval setting (Not set in units of 1μs)
Communication cycle interval setting (Set in units of 1μs)
For the setting procedure for the master station, refer to the following.
MELSEC iQ-R CC-Link IE TSN User's Manual (Application)
A profile is required for each of the model names of the modules to be used.
Open the "CC-Link IE TSN Configuration" window.
Select the module in "Module List" and drag it to the list of stations or the network map.
An assignment setting row is added to the station list, the total number of stations is increased, and the selected module
is added to the network map.
Set items in the station list if necessary.
Click the [Close with Reflecting the Setting] button to complete the setting process and close the window.
• The setting operation can be performed with a general-purpose profile. In that case, select "General
Remote Station" from the "Module List", and then drag and drop it to the station list or the network map.
• A module can also be added to the station list by copying and pasting the model name. In addition, multiple
modules can be selected by dragging over model names and copied and pasted collectively. However,
since the same value is pasted for the station numbers, the station numbers must be changed to avoid
7 PARAMETER SETTING
7.1 Network Configuration Setting
Value that can be set
125μs or more and 4ms or less