Setting the indoor unit address
By considering the entire installation configuration connecting to one ACP, set the address to
each indoor unit not to be overlapped. 00~FF in hexadecimal can be set to the indoor unit ad-
Assigning indoor and outdoor unit number
• If the outdoor unit product is Multi V, it is recommended
to assign the address by setting the first digit of the
address as the number of the outdoor unit, and classify-
ing the second digit as the number or the indoor unit, for
easy composition and classification of the system.
The following example sets the address to the indoor unit.
When the ACP is interconnected with the AC Manager, the ventilator can be installed together
The above figure shows the example that sets the addresses of 30 and 31 to the ventilators and
connects to the ACP.
How to set the central control address of the indoor unit
• The central control address setting method may be different for each indoor unit product or
remote control type, so set the address by referring to the manual of the indoor unit prod-
uct or wired remote controller.