Setting whether to use the power display function
LG ACCS, which is the operation program of the ACP, provides the power display interface func-
tion that can check and manage the power consumption of the air conditioner indoor unit con-
nected to the ACP.
Power display interface
• To use the power display interface function, the power distribution indicator needs to be
interfaced by being connected to PI485 which is connected to the ACP
• Please refer to the corresponding product manual for installation and usage of the power
distribution indicator and PI485.
When the power distribution indicator is installed and if you want to use the power distribution in-
dicator interface function, whether to use shall be set in the ACP. Change whether to use the
power display function as follows:
- When you press the 'SET' button of the ACP, menu screen will be displayed.
Use up and down (▲, ▼) buttons to select [Contents], and press "SET" button again.
While [PDI] is selected, if you press "SET" button, it will display the screen to set whether to
use the power display function.
- Use up and down (▲, ▼) buttons to set whether to use the schedule function. If you press up
(▲) button, it will be set to use the schedule function, and if down (▼) button is pressed, it will
be set to not to use the schedule function.
Example of setting to use the
power display function