Operating ACP with ACCS
Current operation status and power control setting (graph type)
Power control setting
On the right side of the peak operation control screen, there is a setting category that can set
the desired power consumption with the units of percentage (%).
When it exceeds the value set here, the air conditioner is operated in peak operation function
periodically according to the peak operation rule.
Target Operating Rate: sets the desired power consumption to operate peak operation func-
Cycle: sets the peak operation period (It can be set in the range of 5~15 min., and it can be
adjusted in the units of 1 min.)
• Set the peak during peak operation state or run the peak operation after setting the peak.
• If peak operation is not run after setting the peak, the actual peak operation ratio will not be
Current operation status is displayed in the left side of
the peak operation control screen, and there is a graph
that can set power control function. To change the peak
operation ratio, you can drag
the desired operation ratio.
tion in the units of percentage (%). (It can be set in the range of
0~100% of the maximum possible power consumption, and it can be
adjusted in the units of 1 %.)
mark with mouse to set