Changing indoor unit information
Outdoor unit and indoor unit capacity
• When peak/demand control function is used, the indoor unit capacity must be input in the
units of Watt.
• The air conditioner power consumption can be controlled not to exceed the set value
through this value.
Indoor unit power consumption marking method (unit: Watt)
• Power consumption of nth indoor unit =
Add/delete outdoor unit
To add an indoor unit, press [Add an outdoor] button.
Add outdoor unit, and change outdoor unit information as necessary.
Input the number of the connected indoor units, and when [Apply] button
is pressed, it will ask the first address of the indoor unit to be added, and
it will add the indoor units by the number of the indoor units to be added
by finding an empty address from the input address one by one.
When you select an outdoor unit and press [Outdoor delete] button, the
corresponding outdoor unit will be deleted.
At this time, the indoor units connected to the selected outdoor unit will
be deleted as well.
You can change the name of the indoor unit, central control ad-
dress, and indoor unit capacity. After changing the information,
you must press [Apply] button.
(Outdoor unit power consumption + Total power consumption of
the indoor unit) x power consumption of nth indoor unit
Operating ACP with ACCS
Total power consumption of indoor unit