Operation ratio control setting (graph type)
Demand control setting
• Demand control is set by the AC Manager connected outside, so the categories such as
desired operation ratio, operation conversion period, etc. may not be set in LG ACCS pro-
When cooling/heating is not running well
• Set the desired operation ratio to be above 70~80% in AC Manager. Otherwise, cooling or
heating may not run well.
It displays the operation ratio controlled by the de-
The operation ratio of the outdoor capacity control
method is set to the following 9 stages.
9 stages of the operation ratio: 0, 40, 45, 50, 60, 70,
80, 90, 100%
Operating ACP with ACCS