Outdoor unit capacity control method
Cooling/heating performance may be controlled by outdoor unit capacity control, and the cool-
ing/heating performance for VIP room may be maintained by selecting outdoor units not to be ap-
plied in the peak group setting screen.
To control peak operation ratio, click 'Peak Control' menu at the top of LG ACCS.
When you click 'Peak Control' menu, the following control screen appears.
(When outdoor unit capacity control method is selected in peak group setting screen)
When cooling/heating is not running well
• Check the Target Operating Rate setting of peak power control.
• Cooling or heating may not run well because of the Target Operating Rate.
• If the wind from the air conditioner is not cool or warm, raise the Target Operating Rate or
stop peak operation.
Operating ACP with ACCS