Operation ratio control setting (graph type)
There is a graph that can set the peak operation ratio control function.
To change the peak operation ratio, you can drag ◀ mark with mouse to set the Target Oper-
The operation ratio of the outdoor capacity control method can be set to the following 9
9 stages of the operation ratio: 0, 40, 45, 50, 60, 70, 80, 90, 100%
Power control setting
On the right side of the peak operation control screen, there is a setting category that can set
the desired power consumption with the units of percentage (%).
It controls the performance of the outdoor unit not to exceed the value set here.
Desired operation ratio: sets the desired power consumption to run the peak operation func-
tion in the units of percentage (%).
(9 stages of the operation ratio: 0, 40, 45, 50, 60, 70, 80, 90, 100%)
• Set the peak during peak operation state or run the peak operation after setting the peak.
• If peak operation is not run after setting the peak, the actual peak operation ratio will not be
Operating ACP with ACCS