MA REMOTE CONTROLLER
[ 5 ]
<Table1> Function setting options
Automatic recovery after
When the settings are completed, press the
data from the remote controller to the indoor units.
When the transmission is successfully completed, the screen will return to the
Function setting screen.
note: • Make the above settings only on Mr. Slim units as necessary.
• The above function settings are not available for the City Multi
• Table 1 summarizes the setting options for each mode number.
Refer to the indoor unit Installation Manual for the detailed infor-
mation about initial settings, mode numbers, and setting num-
bers for the indoor units.
• Be sure to write down the settings for all functions if any of the
initial settings has been changed after the completion of installa-
Enable (Four minutes of standby time is
required after the restoration of power.)
Average temperature reading of the indoor
units in operation
Thermistor on the indoor unit to which the
remote controller is connected (fixed)
Built-in sensor on the remote controller
Connected (without outdoor air intake by
the indoor units )
Connected (with outdoor air intake by the
indoor units )
220 V, 230 V
Enable (Automatically the unit achieves ef-
fective energy saving operation.)
Silent mode (or standard)
Standard (or High ceiling 1)
High ceiling (or High ceiling 2)
(or the vane setting No.3 is effective.)
Equipped with vanes
(The vane setting No.1 is effective.)
Equipped with vanes
(The vane setting No.2 is effective.)
button to send the setting
Set "Grp." for the Unit number.
These settings apply to all the con-
nected indoor units.
Set "1, 2, 3, 4, or All" for the Unit
number.These settings apply to each
• If "1, 2, 3, or 4" is set for the Unit
number, the settings apply only to
the specified indoor unit regardless
of the number of connected indoor
units (one through four units).
• If "ALL" is set for the Unit number,
the settings apply to all the connect-
ed indoor units regardless of the
number of connected indoor units
(one through four units).