[ 3 ]
[ 4 ]
Select the menu with the F4 button.
Default → Area → Direct/Indirect → Default...
Default: The vanes move the same as during normal operation.
During cooling mode, all of the vanes move to the horizontal airflow direc-
During heating mode, all of the vanes move to the down airflow direction.
Area: The vanes move to the down airflow direction toward areas with a
high floor temperature during cooling mode and toward areas with a low
floor temperature during heating mode. Otherwise, the vanes move to the
horizontal airflow direction.
Direct/Indirect: The vanes automatically move relative to the areas where
persons are detected.
The vanes operate as indicated in the following table.
When Direct/Indirect is selected, set each air outlet.
Select the air outlet with the F1 or F2 button, and change the setting with
the F4 button.
After changing the settings for all of the air outlets, press the
save the settings.
* In order to enable this function, the airflow direction must be set to "Auto".
MA REMOTE CONTROLLER
horizontal → swing
downward → horizontal