1 GETTING STARTED
Open the Display Properties window through the Site List tree as shown. The Display Properties window opens with a
status indicator on the lower left of the EnerVista UR Setup window.
If the status indicator is red, verify that the Ethernet network cable is properly connected to the Ethernet port on the
back of the relay and that the relay has been properly setup for communications (steps A and B earlier).
If a relay icon appears in place of the status indicator, than a report (such as an oscillography or event record) is open.
Close the report to re-display the green status indicator.
The Display Properties settings can now be edited, printed, or changed.
See chapter 4 in this manual or the EnerVista UR Setup Help File for information about the using the EnerVista UR
Setup software interface.
QUICK ACTION HOT LINKS
The EnerVista UR Setup software has several quick action buttons to provide instant access to several functions that are
often performed when using L90 relays. From the online window, users can select the relay to interrogate from a pull-down
window, then click the button for the action they want to perform. The following quick action functions are available:
View the L90 event record
View the last recorded oscillography record
View the status of all L90 inputs and outputs
View all of the L90 metering values
View the L90 protection summary
Generate a service report
Quick action hot links
Expand the site list by double-clicking
or selecting the +/– box.
Communications status indicators:
Green = OK
Red = No communications
UR icon = report is open
L90 Line Current Differential System
1.3 ENERVISTA UR SETUP SOFTWARE
1.3.5 CONNECTING TO THE L90 RELAY