REMOTE DPS INPUT 1
Remote double-point status inputs are extracted from GOOSE messages originating in the remote device. Each remote
double point status input must be programmed to replicate the logic state of a specific signal from a specific remote device
for local use. This functionality is accomplished with the five remote double-point status input settings.
REM DPS IN 1 ID: This setting assigns descriptive text to the remote double-point status input.
REM DPS IN 1 DEV: This setting selects a remote device ID to indicate the origin of a GOOSE message. The range is
selected from the remote device IDs specified in the Remote devices section.
REM DPS IN 1 ITEM: This setting specifies the required bits of the GOOSE message.
The configurable GOOSE dataset items must be changed to accept a double-point status item from a GOOSE dataset
(changes are made in the
items configured to receive any of "GGIO3.ST.IndPos1.stV" to "GGIO3.ST.IndPos5.stV" will accept double-point status
information that will be decoded by the remote double-point status inputs configured to this dataset item.
The remote double point status is recovered from the received IEC 61850 dataset and is available as through the
Ip 1 BAD
RemDPS Ip 1 INTERM
used in breaker or disconnect control schemes.
a) DNA BIT PAIRS
DNA- 1 BIT PAIR
Remote outputs (1 to 32) are FlexLogic operands inserted into GSSE/GOOSE messages that are transmitted to remote
devices on a LAN. Each digital point in the message must be programmed to carry the state of a specific FlexLogic oper-
and. The above operand setting represents a specific DNA function (as shown in the following table) to be transmitted.
Table 5–28: IEC 61850 DNA ASSIGNMENTS
IEC 61850 DEFINITION
REMOTE DPS INPUTS
REM DPS IN 1 ID:
REM DPS IN 1 DEV:
REM DPS IN 1 ITEM:
REM DPS IN 1
CONFIGIGURABLE GOOSE 1(16)
RemDPS Ip 1 OFF
RemDPS Ip 1 ON
REMOTE OUTPUTS DNA BIT PAIRS
DNA- 1 OPERAND:
DNA- 1 EVENTS:
IEC 61850 TEST MODE
IEC 61850 CONF REV
L90 Line Current Differential System
5.8.7 REMOTE DOUBLE-POINT STATUS INPUTS
REMOTE DPS INPUT 1(5)
Range: up to 12 alphanumeric characters
Range: Remote Device 1 to Remote device 16
Range: None, Dataset Item 1 to Dataset Item 32
Range: Enabled, Disabled
IEC 61850 PROTOCOL
CONFIG GSE 1 DATASET ITEMS
FlexLogic operands. These operands can then be
REMOTE OUPUTS DNA- 1(32) BIT PAIR
Range: FlexLogic operand
Range: Disabled, Enabled
5.8.8 REMOTE OUTPUTS