Toolbar: QUICK VIEW ON/OFF
At anytime while using the tabs to view system details, the summary of the UPS Input, Output, and DC Bus can be viewed
by pressing the Q. VIEW button (Button will display Q. VIEW ON). The illustration below highlights the critical features of
the Quick View display.
Exit Quick View by pressing the Q. VIEW button again. (Button will display Q. VIEW OFF)
TABLE 12.3 – QUICK VIEW DISPLAY
Displays Vin, Vout, and Vbyp for all three phases
Changes voltage display mode: Press repeatedly to display sequentially the voltage as: Line-to-Line
(LL), Line-to-Neutral (LN), and Voltage as a % of rated Voltage (%).
The highlighted icon indicates the voltage display mode.
Displays output current for all three phases.
Changes current display mode: Press repeatedly to display alternately the current in Amps (A), or as a %
of rated current (%).
The highlighted icon indicates the current display mode.
Displays DC Bus voltage, Battery voltage, and Battery discharge current.
FIGURE 12.9: QUICK VIEW DISPLAY
4400 Series Installation and Operation Manual – 64527-008