4400 SPECIFICATIONS: 15–30kVA w/ Internal Battery Backup and/or MBS
Optional Matching Battery Cabinets
Optional Matching MBS/PDU
1 - Requires adjustment of factory/service adjustable parameters.
Minimum front clearance for unobstructed airflow is 20 inches. However, minimum front clearance when physically
accessing the UPS must be at least the width of the front door of the UPS, or per NEC 110.34(A)(36 in./900 mm) and local
requirements, whichever is greater.
Approximate weights for dual-input units. Actual weights may vary depending on exact UPS configuration.
UL 1778, CUL, NEC (NFPS-70), CE, IBC, CBC, ANSI C62.41 (IEEE 587), NEMA/PET-1993,
OSHA, ISO9000, ISO 14001:2004.
4400 Series Installation and Operation Manual – 64527-008