• No response is also returned in the case of broadcast communication.
• Error response (Response message)
a. Slave address
H80 + Function
• Error code list
ILLEGAL DATA ADDRESS
ILLEGAL DATA VALUE
An error response is not returned in the following cases:
(a) Function code H03 (reading data of holding registers)
When the number of registers is specified as one or more and there are one or more holding registers from which data can be read
(b) Function code H10 (writing data to multiple holding registers)
When the number of registers is specified as one or more and there are one or more holding registers to which data can be written.
In other words, when function code H03 or H10 is used and multiple holding registers are accessed, an error response is not returned even if a
nonexistent holding register or holding register that cannot be read or written from/to is accessed.
• An error response is returned if none of the accessed holding registers exist. When an accessed holding register does not
exist, the read value is 0 and the written data is invalid.
• Error detection of message data
The following errors are detected in message data from the master. The inverter output is not shut off even if an error is
Error check items
Message frame error
CRC check error
• The LF signal can be assigned to an output terminal by setting any of Pr.190 to Pr.195 (Output terminal function selection).
Changing the terminal assignment may affect other functions. Set parameters after confirming the function of each terminal.
• The following shows the MODBUS registers for system environment variables (read/write), real time monitor items (read),
parameters (read/write), faults history data (read/write), and model information monitor items (read).
c. Exception code
Set the address received from the master.
The function code requested by the master and H80 is set.
The codes in the following table are set.
The query message from the master has a function code that cannot be handled by the slave.
The query message from the master has a register address that cannot be handled by the
(No parameter, parameter cannot be read, parameter cannot be written)
The query message from the master has data that cannot be handled by the slave.
(Out of parameter write range, a mode is specified, or other error)
The data received by the inverter is different from the
specified parity (Pr.120 setting).
The data received by the inverter is different from the stop
bit length (Pr.120) setting.
The next data has been sent by the master before the
inverter completes receiving the preceding data.
The data length of the message frame is checked, and an
error is generated if the received data length is less than
An error is generated if the data in the message frame
does not match the calculation result.
When this error occurs, Pr.343 is
incremented by one.
When this error occurs, the LF signal is
5.11 (N) Communication operation parameters