NOTICE Risk of improper installation. Can cause equipment damage. Only a qualified service professional should install these products. Emerson recommends having an Emerson Network Power ® Liebert Services representative perform the installation in large UPS’s.
Important Safety Instructions Page intentionally left blank. ™ ® ™ Liebert IntelliSlot Unity Card User Manual...
™ cards. Each card employs the Emerson Protocol to monitor and manage a wide range of operating parameters, alarms and notifications about power, distribution and cooling equipment. The cards also communicate with Building Management Systems and Network Management Systems. Liebert IntelliSlot Unity cards support monitoring of sensors to improve system reliability and efficiency.
Passwords Immediately for details. SNMP Support The Liebert IntelliSlot Unity card enables SNMP management of Liebert equipment. To integrate the card into a SNMP implementation, import or compile the Liebert Global Products MIB on the network management station (NMS).
Introduction Modbus TCP and Modbus RTU Support The Liebert IntelliSlot Unity card supports Modbus TCP and Modbus RTU for the full range of information available from the managed device. The Modbus protocol mapping document, SL-28170, is available at Liebert’s Web site: www.liebert.com...
Introduction Page intentionally left blank. ™ ® ™ Liebert IntelliSlot Unity Card User Manual...
2.4 - Installing Multiple Liebert IntelliSlot Unity Cards in a System. 2.1 Installing the Liebert IntelliSlot Unity Card The Liebert IntelliSlot Unity card may be installed at the factory or field-installed. To perform a field-installation: 1. Find the Liebert IntelliSlot bay on your Liebert equipment—It may have a plastic cover.
Boot Mode as described in Static IP on page 8. Connect an RJ-45 cable to the card and it will receive an IP address from the DHCP server. Contact the DHCP administrator to obtain the IP address using the Liebert IntelliSlot Unity card’s MAC address. The MAC address is printed on the card’s faceplate.
1. Find the serial cable from the building management system. If it already has an RJ-45 connector on the end, determine whether it uses the same pin-out as the Liebert IntelliSlot Unity card’s connector. If the pin-out is the same as the Liebert IntelliSlot Unity card connector’s pin-out, skip to Step 7.
5. Be careful not to break the wires. 6. Repeat Step 3 with the negative terminal and the black wire. 7. Plug the cable into the 485 RJ-45 port on the Liebert IntelliSlot Unity card. 2.2 Change User Names and Passwords Immediately...
Password 2.3 Configure the Card The Liebert IntelliSlot Unity card requires minor configuration, such as choosing the IP/Web communication interface, serial RS-485 communication interface, or both. The default for IP/Web communication is IPv4, but this can be changed to IPv6 for greater security; contact your network administrator to determine whether it is compatible with your network.
The default node ID for a Liebert IntelliSlot Unity card is 0, so the second card should use 1 or 2 preferably, or 127 if necessary. Contact your system administrator about the proper node ID for the second card, then perform the steps below.
Installation 2.5 Security Best Practices The default settings on the Unity card support a fast installation and start-up to get basic communication services up and running quickly. Proper security of critical infrastructure equipment requires proper configuration of ALL communication services. This section summarizes the settings to examine to reduce the risk of unauthorized access to critical infrastructure equipment through a Unity card.
YDN23 Settings Only to prevent changes to the device 5.5.4 - Protocols—YDN23 Folder through the YDN23 interface. Enable/disable the Emerson Protocol which is used by Emerson Network Power 5.4.6 - Configuration—Emerson Emerson Protocol Settings management applications for accessing Protocol Folder device data.
Enable Communication Protocols 3.0 Enable Communication Protocols The Liebert IntelliSlot Unity card will communicate with equipment and third-party systems over these protocols: • BACnet IP • BACnet MSTP • Modbus TCP • Modbus RTU • SNMP • YDN23 NOTE No more than two protocols may be enabled on one card.
Enable Communication Protocols 5. Configure the protocols selected. See 5.0 - Editing the Liebert IntelliSlot Unity Card Configuration. 6. Restart the card (See 5.7 - Communications—Support Folder). a. Select Communications tab > Support. b. Enable the commands. c. Click Restart.
Enable Communication Protocols 184.108.40.206 Configure Modbus TCP 1. Select the Communications tab > Protocols > Modbus TCP. 2. Click Edit and enter a User name and password if required. 3. Set the Limit Network Access Type by choosing from the drop-down list (Open/Same Subnet/Trusted IP List).
Enable Communication Protocols 220.127.116.11 Configure Modbus RTU 1. Select the Communications tab > Protocols > Modbus RTU. 2. Click Edit and enter a user name and password if required. 3. Set the Node ID and the Baud Rate. • The Node ID defaults to 1, but must have a value from 1 to 255 that is unique among devices connected through the RS-485 interface.
2. Click Edit and enter a user name and password if required. 3. Enter the Managed Device Write Access level (Read Only or Read/Write). This determines a user’s ability to change settings in the Liebert IntelliSlot Unity card. 4. Choose the BACnet interface: BACnet IP or BACnet MSTP.
2. Click Edit and enter a User name and password if required. 3. Set the BACnetIP/Port Number. If the Liebert IntelliSlot Unity card is on a different subnet (a possibility when the monitored units are part of a Liebert SiteScan network or other third-party monitoring service): a.
Enable Communication Protocols 18.104.22.168 Configure BACnet MSTP Protocol NOTE Contact your system administrator if you are uncertain about the settings. 1. Select Communications tab > Protocols > BACnet MSTP. 2. Click Edit and enter a user name and password if required. 3.
Enable Communication Protocols 3.1.3 Enable SNMP SNMPv1/v2c and SNMPv3 are enabled by default. The protocols may be configured or their default values may be accepted. Authentication Traps are not enabled by default. The default Heartbeat Trap interval is 24 hours; this can be disabled or the interval may be changed. 1.
SNMPv3 Users or SNMPv1/v2c Trap and Access settings must be made before SNMP access or notifications can occur. The Liebert IntelliSlot Unity card permits up to 20 SNMPv3 Users, up to 20 SNMPv1 Trap targets, and up to 20 SNMPv1/v2c Access addresses.
Enable Communication Protocols 22.214.171.124.2 Configure SNMPv3 User Settings The settings must be made for each user who will receive notifications. 1. Select Communications tab > Protocols > SNMP > SNMPv3 Users Setting (20) > SNMPv3 Users Setting (1). 2. Click Edit and enter a User name and password if required. 3.
Enable Communication Protocols 126.96.36.199.3 Configure SNMPv1 Trap Settings 1. Select Communications tab > Protocols > SNMP > SNMPv1 Trap (20). 2. Click Edit and enter a User name and password if required. 3. Enter the information and set the permissions appropriate to the user, Figure 3-10. For descriptions of the settings, see 188.8.131.52 - SNMPv1 Trap Folder.
Enable Communication Protocols 184.108.40.206.4 Configure SNMPv1/v2c Access Settings 1. Select Communications tab > Protocols > SNMP > SNMPv1/v2c Access (20) > SNMPv1/v2c Access (1). 2. Click Edit and enter a User name and password if required. 3. Enter the information and set the permissions appropriate to the user, Figure 3-10. For description of the settings and options, see 220.127.116.11, SNMPv1/v2c Access Folder, page 66.
Enable Communication Protocols 3.2 Download Protocol Mappings The Liebert IntelliSlot Unity Card’s permits downloading files listing information available from a managed device for each enabled protocol. The listings identify the data available from the device and how that data will be represented, or mapped, into a particular protocol.
Enable Communication Protocols Page intentionally left blank. ™ ® ™ Liebert IntelliSlot Unity Card User Manual...
Tab Menus The Liebert IntelliSlot Unity card has two tabs by default: the Managed Device tab, which will display the name of the monitored equipment, and the Communications tab. A third tab, the Sensor tab, appears if Liebert SN sensors have been installed.
Liebert IntelliSlot Unity Card Web Page Layout Detail Displays detailed information about the device based on the menu selection made in the Tab Menu area. Edits to the device and its configuration are made in this section. Figure 4-1 Web page sections, UPS example...
Liebert IntelliSlot Unity Card Web Page Layout Figure 4-3 Managed Device Web page without sensors Sensor Tab not displayed Sensor Status not displayed 4.2 Help Text Each Web page shown by the Liebert IntelliSlot Unity-DP card has informational text that is revealed by hovering a mouse pointer over the icon to the left of the Status, Events or Settings row, as shown below.
Liebert IntelliSlot Unity Card Web Page Layout Figure 4-4 Help text on mouse-over Hovering a mouse pointer over the icon reveals information about that entry. Help text about the System Input Nominal Frequency entry on the Managed Device Tab, Input Menu.
Menus on the Managed Device tab list only data that is relevant to the equipment being monitored. For example, menus shown by a Liebert IntelliSlot Unity card installed in a UPS differ from menus shown by a card installed in Thermal Management equipment. Information on those menus will also differ depending on the equipment the card is installed in.
Shows information needed for maintenance or Agent Manufacture Date troubleshooting and shortcuts to reboot the card, reset the (Firmware Agent Hardware Version Liebert IntelliSlot Unity card to its factory defaults and to Update also GDD Version update the card’s firmware. on page 75)
Liebert IntelliSlot Unity Card Web Page Layout 4.5 Sensor Tab Menus—Shown Only if a Sensor is Connected When Liebert SN sensors are installed and connected to the sensor port on the Liebert IntelliSlot Unity card, the Sensor tab appears. It contains folders showing an overview of the installed sensors, the event status of the sensors, download links for log files and sensor configuration settings as detailed below.
Liebert IntelliSlot Unity Card Web Page Layout 4.5.1 Sensor Tab Summary Page The Sensor tab Summary Page shows the status of all installed sensors, details about any selected sensor and a Setting pane that permits changing a sensor’s label, thresholds if applicable, alarm configuration and acknowledging alarms and events.
Liebert IntelliSlot Unity Card Web Page Layout Selecting a sensor displays details for that sensor. The content of the details section is specific to the type of sensor selected. For example, a temperature sensor would show the temperature of the area where it is installed and a door sensor would show whether the door is open.
Liebert IntelliSlot Unity Card Web Page Layout 4.6 Changing Sensor Order Sensors are listed in the order they are installed. The order can be changed to put sensors deemed more important at the top of the list. To change the order of the sensor list: 1.
5.0 Editing the Liebert IntelliSlot Unity Card Configuration The Web-based interface can be used to change settings for the Liebert IntelliSlot Unity card and for the monitored equipment. The following steps apply to making changes in all sections of the Liebert IntelliSlot Unity card.
The Communications tab’s Downloads folder contains no configurable settings. The folder displays links to download logs of third-party protocols that are enabled on the Liebert IntelliSlot Unity card. The logs help in configuring and troubleshooting communication between the Network Management or Building Management Systems being used to monitor the managed device.
Editing the Liebert IntelliSlot Unity Card Configuration 5.4.1 Configuration—System Folder The System subfolder displays general information about the monitored and managed device and the display of some data. Refer to Figure 5-2. The data displayed is set by the user and can assist in troubleshooting.
Editing the Liebert IntelliSlot Unity Card Configuration 5.4.2 Configuration—User Folder The User subfolder displays the administrator’s and general user’s name and password. Each can be changed. The default user name and password for the administrator are Liebert and Liebert. The defaults for the general user are User and User.
Editing the Liebert IntelliSlot Unity Card Configuration 18.104.22.168 IPv4/IPv6 The IPv4 and IPv6 settings determine which Internet Protocol will be used for communication over the network connected to the Ethernet port. IPv4 and IPv6 networks will run in parallel (dual-stack network), but the protocols are different.
Editing the Liebert IntelliSlot Unity Card Configuration Static IP Address Network address for the interface. Prefix Length Prefix length for the address that divides a network into manageable segments. Default Gateway IP address of the gateway for network traffic destined for other networks or subnets.
Editing the Liebert IntelliSlot Unity Card Configuration 5.4.4 Configuration—Web Server Folder The Web Server Settings permits making some security settings, such as HTTP or HTTPS, and password enabling. Web Server Settings Web Server Protocol Select the operation mode of the Web Server (HTTP, HTTPS) HTTP Port Standard web port not encrypted.
Editing the Liebert IntelliSlot Unity Card Configuration Figure 5-5 Remote write access disabled indicator Session Idle Timeout The interval the software will wait before logging off a user unless there is user activity (Default is 5 min.) 22.214.171.124 Certificate When the Web Server Protocol is configured to use HTTPS communications, all web-server communication with all browsers is encrypted and validated based upon the security algorithms and validity checks specified in the SSL certificate that is currently-installed in the card.
Editing the Liebert IntelliSlot Unity Card Configuration Certificate Settings Generate Self-Signed SSL Certificate Mode Method used to generate a self-signed SSL certificate. Options are: • Use Default Values = the values used in place of the user-configurable fields are the same as those used when the original SSL certificate was generated by the card on first power-up.
® LIFE Technology, a remote monitoring and diagnostic service for Emerson Network Power units. The LIFE settings are for use by trained Emerson Network Power personnel only and require no user changes. For information about the LIFE settings, refer to Appendix A - Configuration Folder—LIFE ™...
Editing the Liebert IntelliSlot Unity Card Configuration 5.4.7 Configuration—Messaging Folder The Messaging subfolder permits enabling email and text messaging about events. The subfolder also contains a test to determine if email and text messages can be successfully sent. Settings for the two messaging methods permit specifying who gets the messages, the format or the messages and other details.
Editing the Liebert IntelliSlot Unity Card Configuration 126.96.36.199 Email Selections in Email determine how the card sends emails about events. Email Settings Email From Address Sender’s email address. In most cases this will be the email address of the person to whom replies should be sent.
Editing the Liebert IntelliSlot Unity Card Configuration SMTP Connection SMTP server connection type. Determines the capabilities of the SMTP server. Options are: • Clear = Do not use encryption • SSL/TLS = Encryption using SSL/TLS connection • STARTTLS = SSL/TLS encryption initiated using STARTTLS.
Editing the Liebert IntelliSlot Unity Card Configuration Consolidation Time Limit If Event Consolidation is enabled, a message will be sent when 'Consolidation Time Limit' seconds has passed since the first buffered event was received. Consolidation Event Limit If Event Consolidation is enabled, a message will be sent when the number of buffered events reaches the ‘Consolidation Event Limit.’...
Editing the Liebert IntelliSlot Unity Card Configuration SMTP Server Address Fully-qualified domain name or IP address of the server used for relaying SMS messages. Note: If using a server name, a DNS server may need to be configured under Network Settings.
188.8.131.52 Messaging Test Selections here permit testing the setup for email and SMS messages. If the test fails, incorrect settings should be changed to ensure that the Liebert IntelliSlot Unity card sends proper notifications if an event should occur. ™...
5.5 Communications—Protocols Folder The Protocols folder displays the types of protocols that may be enabled for a Liebert IntelliSlot Unity card. Not all protocols are available at the same time. Some protocols may not be available for some types of managed devices (see 1.2 - Compatibility With Other Emerson Products and Communication...
Editing the Liebert IntelliSlot Unity Card Configuration 5.5.1 Protocols—BACnet Folder BACnet Settings Managed Device Write Access Enable or Disable the BACnet server to write to the managed device. BACnet Interface BACnet server interface: BACnet IP or BACnet MSTP. Device Object Instance Number The instance number (0-4194302) of the BACnet server's device object.
Editing the Liebert IntelliSlot Unity Card Configuration 184.108.40.206 BACnet IP Folder BACnet IP Settings BACnet IP Port Number The port for the BACnet server's UDP/IP connection. Register as Foreign Device Enable or Disable registration as a foreign device. IP Address of BBMD...
The Modbus TCP permits connection to the card by: • any client (Open) permits communication by any IP address • clients on the same subnet as the Liebert IntelliSlot Unity card • clients with specific IP addresses (Trusted IP Lists); only five addresses are permitted...
Editing the Liebert IntelliSlot Unity Card Configuration 220.127.116.11 Modbus RTU Folder Modbus RTU Settings Node ID Modbus Server ID for the interface; obtain from network administrator. Baud Rate Communication rate (9600, 19200, 38400) Parity Check The communication parity check (None, Even, Odd) 5.5.3...
Editing the Liebert IntelliSlot Unity Card Configuration SNMP v3 Enable Enable or Disable SNMPv3. Authentication Traps When enabled, an Authentication Trap is sent if an SNMP host tries to access the card via SNMP, but either the host address is not in the SNMP Access Settings or it is using the wrong Community String.
Editing the Liebert IntelliSlot Unity Card Configuration 18.104.22.168 SNMPv3 User Folder The Liebert IntelliSlot-Unity card supports up to 20 SNMPv3 users. The top level page has a table with settings for all 20. The page displays a link to edit the table columns displayed for each SNMPv3 user. The same settings may be accessed by clicking on a folder for a user, such as SNMPv3 User .
Editing the Liebert IntelliSlot Unity Card Configuration SNMPv3 Privacy Cryptographic algorithm used for encryption. Options are: • None • DES • AES SNMPv3 Privacy Secret Pass phrase or password used for SNMPv3 Get request. This string can be composed of printable characters with the exception of colon, tab, double quote, and question mark.
Editing the Liebert IntelliSlot Unity Card Configuration 22.214.171.124 Editing the SNMPv3 Table The table on the SNMPv3 User Settings  page may be altered to provide more or less information. To do so, click on the command above the table (Click here to edit columns displayed in this table). Put a check mark ( ) in the boxes beside the desired information (see Figure 5-9).
Editing the Liebert IntelliSlot Unity Card Configuration 126.96.36.199 SNMPv1 Trap Folder This page contains settings for network hosts that will receive SNMPv1 traps. Up to 20 trap recipients may be enabled and configured. Like the SNMPv3 pages, the settings for each target may be reached by clicking on the links in the Detail portion of the page or by clicking on the folders for the trap targets.
Editing the Liebert IntelliSlot Unity Card Configuration 188.8.131.52 SNMPv1/v2c Access Folder This page contains settings for network hosts that can access data using SNMPv1/v2c. Up to 20 access hosts can be enabled and configured. Like the SNMPv3 pages, the setting for each host may be reached by clicking on the links in the data portion of the page or by clicking on the folders for the access hosts.
Editing the Liebert IntelliSlot Unity Card Configuration 5.5.4 Protocols—YDN23 Folder The YDN23 protocol supported is based on the YD-T-1363 specification using an RS-485 network connection. YDN23 Protocol settings Managed Device Write Access Enable or Disable the YDN23 server to write to the managed device.
Editing the Liebert IntelliSlot Unity Card Configuration 5.6 Communications—Status Folder The Status folder contains no configurable items. It displays the System Status of the Liebert IntelliSlot Unity card and a list of events that affect the card’s status. A green check mark (...
Editing the Liebert IntelliSlot Unity Card Configuration 5.7 Communications—Support Folder The Support folder permits restarting the Liebert IntelliSlot Unity card, resetting the card to its factory defaults and updating the card’s firmware. Agent refers to the Liebert IntelliSlot Unity card.
Editing the Liebert IntelliSlot Unity Card Configuration Agent Serial Number The card’s serial number Agent Manufacture Date The card’s manufacture date Agent Hardware Version The card’s hardware version GDD Version The card’s GDD version, current when the card’s firmware was installed; the GDD is a proprietary reference document for device data.
Editing the Liebert IntelliSlot Unity Card Configuration 5.7.1 Support—Active Networking Folder Status of the currently active IP network settings for the Liebert IntelliSlot Unity card along with some previous values for troubleshooting IP communication issues. Active Networking Settings Ethernet MAC Address...
Editing the Liebert IntelliSlot Unity Card Configuration StateLess Address AutoConfiguration IPv6 SLAAC is assigned automatically from Router Advertisement, if “A” flag is set, combining Prefix with EUI-64 MAC Link Local Presently used IPv6 Link Local Address IPv6 Default Gateway Presently used IPv6 network address of the gateway for network traffic destined for other networks or...
Editing the Liebert IntelliSlot Unity Card Configuration 5.7.2 Support—Firmware Update Folder The Firmware Update folder supports updating the firmware of the Liebert IntelliSlot Unity card or reverting to an alternate firmware version and configuration (if the current firmware is not the initial load). Firmware Update settings...
Editing the Liebert IntelliSlot Unity Card Configuration Firmware Commands Run Alternate Firmware Return the card's firmware to a version in the alternate area (the version in use before the most recent firmware update). Firmware Update Update the card’s firmware to a new version ™...
6.0 Firmware Updates The Liebert IntelliSlot Unity card has two areas in flash memory for the firmware and the configuration. One area is currently operating on the card. The other area is the previous firmware on the card and is considered an alternate.
Firmware Updates 7. Click the Web button. The firmware-update screen opens. 8. Browse to the firmware file to update, select it and click the Update Firmware button. NOTE Do not navigate away from the Firmware Update screen and do not close the browser once the update begins.
Firmware Updates 6.2 Revert to Alternate Firmware The Liebert IntelliSlot Unity card has two areas in flash memory for the firmware and the configuration. One area is currently operating on the card. The other area is considered an alternate. When a card’s firmware is updated, the previous firmware and configuration are moved to the alternate area.
Firmware Updates Page intentionally left blank. ™ ® ™ Liebert IntelliSlot Unity Card User Manual...
The LIFE sub folder contains settings that affect use of the Emerson ® LIFE Technology, a remote monitoring and diagnostic service for Emerson units. The LIFE settings are for use by trained Emerson Network Power personnel only and require no user changes. Status...
™ Configuration Folder—LIFE Sub Folder Gate Settings Status Description HTTP Transport Result HTTP Transport Result contains the result of the last HTTP transaction. HTTP Transport Error Value HTTP Transport Error value from the last HTTP transaction HTTP Transport Reply Time HTTP transport reply time Connection Result IP connection result...
All rights reserved throughout the world. Specifications subject to changewithout notice. ® Liebert is a registered trademark of Liebert Corporation. All names referred to are trademarks or registered trademarks of their respective owners. SL-52645_REV8_4-16 590-1305-501B Emerson Network Power Liebert www.emersonnetworkpower.com...