In Zone Trigger mode, the options for Multi-Mode are "Enabled" or "Disabled." If enabled, whenever a zone on the
communication device is triggered, a corresponding email message is sent INSTEAD of normal central station
Cover tamper will send email event 8. All communication device system events (such as power loss, low battery, etc.)
are still sent to AlarmNet.
Events used to send email messages are defined on the Honeywell Total Connect web site, and must correspond to
events triggering the hardwired zones.
Multi-Mode (email notification) is intended as a convenience for the user, and does not replace Central Station
reporting of critical events (alarms, troubles, etc.).
Important Information Regarding Primary Account (Prompts 11-13)
Account information is provided by the central station administrator.
Primary City ID
Primary CS ID
Primary Sub ID
Programming for Zone Trigger, 4204 and Two-4204 Modes
Important Information Regarding Multi-Mode
Enable if you want system events sent by email
to the user.
Disable for normal alarm processing.
Enter the 2-digit primary city ID, 01-99
Enter the 2-digit primary central station ID
number, 01-FE (HEX).
Enter the 4-digit subscriber account number,
The module communicates with the control panel
as a 4204 relay module. Enter the appropriate
address. For VISTA-10P, and FA130CP Series
control panels, this must be address 12. For
other controls, see the control panel's
Installation and Setup Guide.
1. The 4204 protocol limits address range to 01-
15. If using 2-4204 mode, the module assigns
the second 4204 to the next higher device
address (e.g., if entering address 12 for the
first 4204, then address 13 is automatically
assigned to the second 4204 module).
Program the control panel accordingly.
2. The device address(es) must be unique from
the "Keypad Address" entered in Prompt 17
and any other address used on the control
Press [Y] to allow the end user to access their
system via a website. Availability of this service
is controlled by the dealer via the web-based
programming tool on the AlarmNet Direct
Applies only to control panels that support Direct
Enables Direct Wire Downloading over IP.
If [N], and if Prompt 15: "Remote Access" is
disabled, skip to Prompt 18: "Supervision."
Section 3: Programming