Installation instructions for WSC sleeve
Falling Object Hazard
Not following Installation Instructions
for mounting your air conditioner can
result in property damage, inJury, or
Mounting hardware provided
The wall opening required for a WSC SLEEVE is 17 Y4'
high by 27 X" wide.
LINTELS must be used in opening of brick veneer and
masonry walls to support the material above the WSC
SLEEVE. The following considerations should also be given:
A. Adjustable SUBBASE (SB) or other unit support must be provided
for panel wall
construction and for walls less than 8" thick.
B. A minimum distance of 1" must be allowed on all sides of
to adjacent wall and floor. Where the subbase is required, the
minimum distance from the floor to the sleeve must be 3
minimize chances ofshort cycling ofthe compressor, the minimum
clearance between the ceiling and the top of the unit should be
24". (See Figure 7).
Minimum Of 24" Required
From Top Of Unit To Ceiling.
1·,··. " "
Minimum Of 1" Spacing
Required On All Sides
••••'.# . . .