9. Place a non-addic algaedde in the basepan to inhibit bac
teria growth. Ensure the algaedde is compatible with wet
coil operation and is not corrosive to the coil.
HIGH PRESSURE AND HIGH TEMPERAnJRE CLEANNG IS NOT RECOMMENDED.
COULD DAMAGE THE ALUMINUM FIN STOCK AND ELECTRICAL
Clearances around the unit should also be checked to make sure
that the intake air and discharge air paths have not become
blocked or restricted.
minimum of eight inches clearance is
needed from unit to furniture, beds, or other objects for proper
operation. Restricted discharge or intake air will reduce the
unit's operational performance. In severe airflow restrictions
damage can occur to unit components such as the compressor,
electric heater or fan motor.
In the event this unit requires repair or servicing beyond what is
covered in this manual, contact an authorized service organiza
To obtain an authorized servicer, contact your sales representa
tive or agency.
SOUNDS AND CONDITIONS
Water trickling sounds
Water is picked up and distributed over the coil. This
improves the efficiency and helps with water removal.
I§] Water dripping
Water will collect in the base pan during high humidity days.
This can cause overflow and drip from the outside of the unit.
The fan cycle switch sets the operational mode of the fan in
the ON position. The fan
run continuously whenever
power is applied in this mode. In the AUTO position, the fan
cycle on and off with the compressor or electric heater.
I§] Starting delay
You may notice a few minutes delay in the starting if you
try to restart the unit too soon after turning it off or if you
adjust the thermostat right after the compressor has shut
off. This is due to a built in delay to protect the compres
7 BUUQN TOUCH
The control can be configured to operate a wide range of
options. The options listed below with the • are the factory
default settings. If these are acceptable, then the unit does not
require any additional configuration and is fully operable.
configure the unit, first select the configuration feature
code setting and then an option code to change from the
factory default setting.
To enter configuration feature mode:
Press and hold the up and clown
arrow keys at the
same time and press the
key twice within a
two (2) second time frame. The display will indicate - -.,
and then release the
key and press the
time. The display will then alternate between
To select a different configuration feature code, press the
key until the desired configuration comes
up. To scroll to a previously viewed configuration codes
Once you have scrolled to the correct feature, then to se
lect the option code for your desired configuration, press
either the up or down key
to scroll through the op
tions of the selected feature code.
To exit configuration mode:
key. Configuration feature mode
will also exit if no keys are pressed for a period of two