3. Installation and wiring
This section describes the precautions to be taken for wiring.
You must use 24V DC power supply.
If the power variation is more than the regular range, you must connect a
constant voltage transformer.
To prevent noise from the power cable, twist the power cable as densely as
possible and connect within the shortest distance.
Provide the power where the noise is lesser. (If there is much noise, connect the
For PLC, I/O machine and power machine, it is required to divide the power as
Where T1, T2: Constant voltage transformer.
Use 2mm² thick power cable to reduce the voltage fluctuation.
Pnet I/F Module 2MLL-PSRA, 2MLL-PSEA User's Guide
Figure 9 – Power wiring