CLIOL(R)824A Relay Output Module
One instance of the L
been assigned per input of the CLIOL824A/CLIOLR824A
Relay Output Module.
Each output object has its own configuration properties,
except for heartbeat configuration, which will be shared
among all objects.
Open Loop Actuator Object
(LonMark Object Type 3)
open-loop sensor object has
Relay Output Command – nviDoSwitch[ ]
This network variable is used to drive the relay output.
It is typically bound to a L
output level ON/OFF, respectively 0 ... 100 %.
0.5 ... 100 %
Table 70 Relay output command values
Value = 0
State = -1
At start-up, i.e., power-up or reset, all nvi's will be initialized
with INVALID, leading the actuator to drive to the configured
safety position after 1 minute.
The default configuration for "Receive Heartbeat" is 300 sec.
If no nvi update is received during this time, the field devices
will go to their configured safety positions.
LON Software Interface Description
control device issuing an
Outputs are switched
according to actual output
as defined for failure behavior