General Safety Information
When performing any work (installation, mounting, start-
up), all instructions given by the manufacturer and in
particular the safety instructions provided in these
Installation and Commissioning Instructions are to be
The Excel 800 System (including the XCL8010 Controller
Module, I/O modules, manual disconnect modules, and
the auxiliary terminal packages) may be installed and
mounted only by authorized and trained personnel.
Rules regarding electrostatic discharge should be
If the Excel 800 System is modified in any way, except by
the manufacturer, all warranties concerning operation
and safety are invalidated.
Make sure that the local standards and regulations are
observed at all times. Examples of such regulations are
VDE 0800 and VDE 0100 or EN 60204-1 for earth
Use only accessory equipment which comes from or has
been approved by Honeywell.
It is recommended that devices are to be kept at room
temperature for at least 24 hours before applying power.
This is to allow any condensation resulting from low
shipping/storage temperatures to evaporate.
The Excel 800 System must be installed in such a
manner (e.g., in a lockable cabinet) as to ensure that
uncertified persons have no access to the terminals.
Investigated according to United States Standard UL916,
Investigated according to Canadian National Standard(s)
C22.2, No. 205-M1983 (CNL-listed).
Safety Information as per
The Excel 800 System is an independently mounted
electronic control system with fixed wiring.
It is used for the purpose of building HVAC control and is
suitable for use only in non-safety controls for installation on
or in appliances.
System transformer Europe: safety isolating
System data as per EN60730-1
Pollution Degree 2,
suitable for use in residential
controls, commercial controls,
in a clean environment.
for mains-powered (16A) controls
for 24 V powered controls
(micro-interruption for the relay
75 °C for all housing and plastic
125 °C in the case of devices
applied with voltage-carrying parts
Tested at 230 VAC,
with the modules in normal
transformers according to
U.S.A. and Canada: NEC Class-2