EAGLE CONTROLLER – INSTALLATION & COMMISSIONING INSTRUCTIONS
General Safety Information
When performing any work, all instructions given by the
manufacturer and in particular the safety instructions
provided in these Installation and Commissioning
Instructions are to be observed. Make sure that the local
standards and regulations are observed at all times.
The EAGLE System (including the EAGLE Controller,
Panel Bus I/O modules, manual disconnect modules, and
auxiliary terminal packages) may be installed and mounted
only by authorized and trained personnel.
It is recommended that devices be kept at room tem-
perature for at least 24 hours before applying power. This
is to allow any condensation resulting from low shipping /
storage temperatures to evaporate.
The EAGLE System must be installed in such a manner
(e.g., in a lockable cabinet) as to ensure that uncertified
persons have no access to the terminals.
In the case of vertical mounting on DIN rails, the EAGLE
controller should be secured in place using a
If the EAGLE System is modified in any way, except by the
manufacturer, all warranties concerning operation and
safety are invalidated.
Rules regarding electrostatic discharge should be followed.
Use only accessory equipment which comes from or has
been approved by Honeywell.
Information as per EN 60730
The EAGLE Controller is a multifunctional non-safety control
device intended for HVAC in home (residential, commercial,
and light-industrial) environments.
The EAGLE Controller is an independently mounted
electronic control unit with fixed wiring.
The EAGLE Controller is suitable for mounting as follows:
in fuse boxes conforming with standard DIN43880, and
having a slot height of max. 45 mm;
in cabinet front doors (using accessory MVC-80-AC2);
on walls (using accessory MVC-80-AC1).
Table 1. Information as per EN 60730
Rated impulse voltage
WEEE: Waste Electrical and Electronic
At the end of the product life, dispose
of the packaging and product in an
appropriate recycling center.
Do not dispose of the device with the
usual domestic refuse.
Do not burn the device.
Standards, Approvals, etc.
Device meets EN 60730-1 and EN 60730-2-9.
Refer to Code of Practice standards IEC 61000-5-1 and -2
The device complies with ETHERNET Protocol versions
The device supports BACnet IP and BACnet MS/TP
communications as per ANSI / ASHRAE 135-2010.
Type 1.C (micro-interruption for
the relay outputs)
housing parts >75 °C
terminals >125 °C