In-room chilled water smart cooling product (175 pages)
Summary of Contents for Huawei NetCol5000-C Series
NetCol5000-C(065, 080) In-row Chilled Water Smart Cooling Product User Manual Issue Date 2020-03-16 HUAWEI TECHNOLOGIES CO., LTD.
Notice The purchased products, services and features are stipulated by the contract made between Huawei and the customer. All or part of the products, services and features described in this document may not be within the purchase scope or the usage scope. Unless otherwise specified in the contract, all statements, information, and recommendations in this document are provided "AS IS"...
The "NOTICE", "CAUTION", "WARNING", and "DANGER" statements in this document do not cover all the safety instructions. They are only supplements to the safety instructions. Huawei will not be liable for any consequence caused by the violation of general safety requirements or design, production, and usage safety standards.
Do not power on the equipment before it is installed or confirmed by professionals. 1.2 Personnel Requirements Personnel who plan to install or maintain Huawei equipment must receive thorough training, understand all necessary safety precautions, and be able to correctly perform all operations.
Metal shavings from drilling may short-circuit boards inside the equipment. Obtain the consent from the customer, subcontractor, and Huawei before drilling. Wear goggles and protective gloves when drilling holes. ...
(Applicable to V200R001C20 and later versions) NOTE Only Huawei service engineers or authorized service engineers are allowed to use the WiFi module. To ensure security, remove the WiFi module immediately after use. ...
Optional: materials that can be purchased from Huawei or any other vendor (if you have ordered the materials from Huawei, you do not need to purchase them elsewhere). For details about the specifications of such materials to be purchased, see the following sections.
Step 3 Check the type and quantity of fittings against the packing list. If fittings are missing or inconsistent with those in the packing list, contact your local Huawei office immediately. ----End Issue 07 (2020-03-16)
If gas emits, the system is normal. Slowly open the exhaust valve to discharge nitrogen and close the valve when there is no airflow through the valve. If no gas emits out of the valve, contact Huawei technical support. Figure 3-15 Checking the nitrogen pressure ----End...
Hot aisle 5 temp/humid The default addresses of T/H sensors purchased from Huawei are 1. Keep the last RS485_R toggle switch at OFF. After the addresses are set, power on the device. On the display's home screen, choose Settings >...
To prevent the effect of misoperation on the system during the O&M, log in as the operator user first before modifying parameters. Confirm with Huawei before modifying parameters that cannot be modified by operator users; otherwise, Huawei will not be liable for any consequences of the unauthorized modification.
Enable the WiFi function. The default status is Disable. Step 3 Tap Submit. ----End 4.4 Startup Download the Service Expert app from Huawei app store and runs on Android. Apply for permission after downloading the app. Step 1 Tap Start on the home screen of the ACC. ...
Service Expert app for initial startup verification. The Service Expert app can be downloaded from Huawei app store and runs on Android. User interfaces displayed in this document correspond to the APP software version V100R001C00B043T007 and are for reference only.
Pay attention to the safety symbols on the equipment and all safety instructions in this document. The safety precautions given in this document do not cover all safety precautions. Huawei will not be liable for any consequence caused by violation of the safety operation regulations and design, production, and usage standards.