In-room chilled water smart cooling product (175 pages)
Summary of Contents for Huawei NetCol5000-C030H90D0
NetCol5000-C(030, 032, 065) In-row Chilled Water Smart Cooling Product User Manual (2019) Issue Date 2020-08-30 HUAWEI TECHNOLOGIES CO., LTD.
Notice The purchased products, services and features are stipulated by the contract made between Huawei and the customer. All or part of the products, services and features described in this document may not be within the purchase scope or the usage scope. Unless otherwise specified in the contract, all statements, information, and recommendations in this document are provided "AS IS"...
The "NOTICE", "CAUTION", "WARNING", and "DANGER" statements in this document do not cover all the safety instructions. They are only supplements to the safety instructions. Huawei will not be liable for any consequence caused by the violation of general safety requirements or design, production, and usage safety standards.
Do not power on the equipment before it is installed or confirmed by professionals. 1.2 Personnel Requirements ● Personnel who plan to install or maintain Huawei equipment must receive thorough training, understand all necessary safety precautions, and be able to correctly perform all operations. ●...
10 kW per cabinet. This brings challenges of heat dissipation, energy saving, and environment protection to the current cooling system. Huawei has developed the in row cooling product for new-generation data centers. Huawei has developed the in row cooling product for new-generation data centers.
● Optional: materials that can be purchased from Huawei or any other vendor (if you have ordered the materials from Huawei, you do not need to purchase them elsewhere). For details about the specifications of such materials to be purchased, see the following sections.
Inspect the cabinet exterior for signs of collision or scratches. If any damage is found, contact the shipping company immediately. Step 3 Check the type and quantity of fittings against the packing list. If fittings are missing or inconsistent with those in the packing list, contact your local Huawei office immediately. ----End 3.3 Installation Process...
If gas emits, the system is normal. Slowly open the exhaust valve to discharge nitrogen and close the valve when there is no airflow through the valve. ● If no gas emits out of the valve, contact Huawei technical support. Figure 3-15 Checking the nitrogen pressure (NetCol5000-C065) Issue 03 (2020-08-30)
Confirm with Huawei before modifying parameters that cannot be modified by operator users; otherwise, Huawei will not be liable for any consequences of the unauthorized modification. ● Only certified pros are allowed to modify the advanced parameters.
Upper limit for dehumid start temperature demand > Upper limit for dehumid close temperature demand 4.5 Startup NO TICE Download the Service Expert app from Huawei app store and runs on Android. Apply for permission after downloading the app. Step 1 Tap Start on the home screen of the ACC. ●...
NO TICE The Service Expert app can be downloaded from Huawei app store and runs on Android. User interfaces are for reference only. ● For offline boot, enter the barcode and the verification code on the mobile phone app.
Pay attention to the safety symbols on the equipment and all safety instructions in this document. The safety precautions given in this document do not cover all safety precautions. Huawei will not be liable for any consequence caused by violation of the safety operation regulations and design, production, and usage standards.